View and Download Dräger Polytron instructions manual online. Transmitters for electrochemical sensors. Polytron Transmitter pdf manual download. View and Download Dräger Polytron instructions for use manual online. ( approved as type P3S). Transmitter for electrochemical Sensors. Polytron The Dräger Polytron® is an intrinsically safe gas detector for the continuous The Polytron consists of two components, the docking station, . Please note – Product designs and specifications are subject to change without notice.
|Published (Last):||9 April 2018|
|PDF File Size:||6.60 Mb|
|ePub File Size:||18.51 Mb|
|Price:||Free* [*Free Regsitration Required]|
For Your Safety For Your Safety Strictly follow the Instructions for Use Any use of the apparatus requires full understanding and strict observation of these instructions.
Repair and general overhaul of the apparatus may only be carried out by trained serv- ice personnel. For further details, see the installation notes.
Dräger Polytron 3000 Instructions Manual
Notes on use in zone The Polytron transmitter may also be connected to other central units if the fol- lowing conditions are met: Polyteon the national regulations concerning electrical equipment in explosion-hazard areas. Installing the transmitter Installing the docking station mznual If the transmitter is to be installed in a Zone 2 explosion-hazard area, select a lo- cation with low exposure to mechanical risk.
Shorten the shield if installed to prevent short-circuiting: Cut excess wires short or 2 Fasten in 4-pin terminal. Polytron Use only a 5 mm Allen key without a ball head.
This current is proportional to the gas concentration. Maintenance Maintenance Maintenance intervals Before starting operation: Use only a 5 mm Allen key without a ball head. Maintenance Calibrating the zero point For all sensors except oxygen sensor: The zero point can be calibrated without the use of nitrogen zero gas when the ambient air polyrton free from measuring gas and other interfering gases.
Polytron 1 Use the calibration adapter. Maintenance 1 Set maintenance switch to left-hand position.
The 4 to 20 mA output changes to measuring mode. Display Equipment fault, Only use a sensor with the gas type, Part No. Splash guard 68 07 Splash guard AC sensor 68 09 Also See for Polytron Instructions manual – 68 pages.
Page of 52 Go. Page 9 – Installing the transmitter in areas subj Page 10 – Installing the transmitters in non-explo Table of Contents Add to my manuals Add.
Intended Use For further details, see the installation notes.
Drager Polytron – Keison Products
Installing The Transmitter In explosion-hazard areas: Installing The Docking Station Installing the transmitter Installing the docking station — If the transmitter is to be installed in a Zone 2 explosion-hazard area, select a lo- cation with low exposure to mechanical risk.
Fitting The Sensor 2 Open the front cover of the service port with an Allen key by turning anticlockwise approx. Start-up — A current between 4 and 20 mA flows through the transmitter during normal op- eration. Maintenance Maintenance Maintenance Maintenance intervals Before starting operation: Replacing The Sensor Allen key approx. Page 18 Maintenance 1 Set maintenance switch to left-hand position.
Page 24 Order No. Page 25 Order No. Page 27 ATEX approval Page 28 ATEX approval Page 29 ATEX approval Page 30 ATEX approval Page 32 IECEx approval Page 33 IECEx approval Page 34 IECEx approval Page 36 UL approval Page 37 UL approval Page 39 CSA – Approval Page 40 CSA – Approval Page 41 CSA – Approval Page 42 CSA – Approval Page 44 Declaration of Conformity Page 45 Declaration of Conformity Page 46 Declaration of Conformity Index Index Index 4 to 20 mA current loop Page 48 Index Ingress protection Comments to this Manuals Your Name.
Enter text from picture: By pressing ‘print’ button you will print only current page. To print the manual completely, please, download it.
Don’t show me this message again. Got it, continue to print. Don’t have an account?